- City Officials
- Mary Zendejas1st District
- Cindy Allen2nd District
- Kristina Duggan3rd District
- Daryl Supernaw4th District
- Megan Kerr5th District
- Suely Saro6th District
- Roberto Uranga7th District
- Al Austin8th District
- Dr. Joni Ricks-Oddie9th District
- Dawn McIntoshCity Attorney
- Laura L. DoudCity Auditor
- Doug HaubertCity Prosecutor
- Tom ModicaCity Manager
- Monique DeLaGarzaCity Clerk
Dr. Joni Ricks-Oddie
Laura L. Doud
City-Wide Elected Officials
Opening a Business
Doing Business With The City
- LBDS Home
- About Us
- Schedule Building Inspection
- Building Permits
- Building & Safety Fee Schedule
- Construction Code Resources and Documents
- Construction & Demolition (C&D) Debris Recycling Program
- Deputy Inspector Program
- Online Permits
- Planning Permits
- Planning Fee Schedule
- Project Plan Review and Submittal Service
- Plan Review Status/Permit Status/Records
- Resources & Forms
- Programs & Projects
Housing & Neighborhood Services
Applications & Forms
Home » Development Services » FAQ » Mechanical Code Questions
Mechanical Code Questions
Condensate from air conditioning equipment and cooling coils shall be collected and discharged to an approved plumbing fixture or disposal area. Condensate shall not drain over a public way. Specific requirements are as follows:
- Condensate must be piped to the sanitary system with an indirect connection into a properly trapped and vented plumbing receptor or directly into its tailpiece; or
- Condensate may be piped to an approved drywell. When condensate is terminated at a drywell, it shall be an indirect connection to a properly constructed drywell. Handouts specifying drywell construction requirements are available at the Development Services Center. Drywells for draining large tonnage systems and for commercial and industrial projects must be engineered and included as part of the approved plans for the project.
Additional requirements for condensate piping to consider are as follows:
- Condensate drain lines shall slope not less then 1/8 inch per ft. or 1 percent slope toward the termination and shall be of an approved corrosion resistant material.
- Condensate drain lines shall be sized in accordance with the California Mechanical Code Section 310.3 or as recommended by the equipment manufacturer.
- When a cooling coil is located in an attic or furred space where damage may result from condensate overflow, an additional water tight pan of corrosion resistant metal shall be installed beneath the cooling coil to catch overflow condensate due to a clogged primary condensate drain, or one pan with a standing overflow and separate secondary drain may be provided in lieu of the secondary pan. The secondary drain shall be piped to a discharge location where it can be readily observed outdoors such as over a door or window.
Dryer moisture exhaust ducts shall be of metal and shall have smooth interior surfaces. Screws or other fasteners shall not be used that will penetrate the duct wall and obstruct the airflow. Dryer moisture exhaust ducts shall only serve clothes dryers. Unless otherwise permitted or required by the dryer manufacturer’s installation instructions and approved by the Authority Having Jurisdiction, domestic clothes dryer moisture exhaust ducts shall not exceed a total combined horizontal and vertical length of 14 feet, including two 90 degree elbows. Two feet shall be deducted for each 90-degree elbow in excess of two.
Interior spaces intended for human occupancy shall be provided with active or passive space heating systems capable of maintaining a minimum indoor temperature of 68 degrees F. at a point 3 feet above the floor on the design heating day.
Not less then 30 inches in depth, width and height of working space and platform shall be provided to service all equipment on the service/access side of the equipment. Clearances to combustibles shall be in accordance with the equipment manufacturer’s listing and installation instructions. Additional clearances may be required by the equipment manufacturer for service, airflow etc. Clearance for gas vents shall be in accordance with the listed vent manufacturer’s installation instructions.
5. What are the requirements for the termination of a bath, kitchen or dryer duct (environmental exhaust duct)?
Environmental exhaust ducts shall terminate a minimum of 3 feet from the property line and 3 feet from openings to the building.
Building & Safety Bureau
|M:||8:00 AM - 4:00 PM|
|T:||8:00 AM - 4:00 PM|
|W:||9:00 AM - 4:00 PM|
|TH:||8:00 AM - 4:00 PM|
|F:||8:00 AM - 4:00 PM|
411 West Ocean Blvd., 3rd Floor
Long Beach, CA 90802